Employs a Copeland scroll compressor to minimize vibration and noise
Optimizes heat-exchange ability by adopting pure copper heat exchanger
Improve heat-exchange ability thanks to a hydrophilic coating that quickly drains water generated below the dew point temperature
Equipped with control board to measure and compute environments, water heater is operated on condition of maximum heating ability and minimum energy consumption.
Heat pump water heater is operated based on cannot
cycle principle. Evaporable refrigerant is exchanged with
hot air in evaporator.
In this process, heat is absorbed and evaporated.
The evaporated heat is inhaled, compressed,
and changed into high temperature and high pressure
refrigerant in compressor.
High pressure refrigerant exchanges heat with water via
the condenser in heat-storage tank. Finally, refrigerant
is liquefied and the water absorbs heat.
Hot water is made through these repeated cyclic process
|Heatpump Operating outdoor temp||℃||7~43|
|Temp setting range||℃||15~65|
|Heatpump heating capacity||kW||3.75|
|Elec. Heater capacity||kW||3.0|
|Electric consumption||kW||Minimum 2.0 / Maximum 3.0|
|Dimension(D X H)||mm||680 X 1,830|
|old water inlet connection||A||15|
|Hot water outlet connection||A||15|
|Electric Supply||-||1 phase, 220V x 60Hz|
|No file is added.|